|Publication number||US3450949 A|
|Publication date||Jun 17, 1969|
|Filing date||Feb 24, 1967|
|Priority date||Feb 24, 1967|
|Publication number||US 3450949 A, US 3450949A, US-A-3450949, US3450949 A, US3450949A|
|Inventors||Inglis Jack S|
|Original Assignee||Kelek Co|
|Export Citation||BiBTeX, EndNote, RefMan|
|Patent Citations (4), Referenced by (10), Classifications (7)|
|External Links: USPTO, USPTO Assignment, Espacenet|
June 17, 1969 J. s. INGLIS FUSE FAILURE DETECTOR Filed Feb. 24, 1967 FIG., I
INVENTOR. JACK S. INGLIS FIG. 3
ATTORNEYS United States Patent U.s. Cl. 317-46 3 Claims ABSTRACT OF THE DISCLOSURE A- multi-vaned pivotal insulating operator is situated between plural fuse actuators, each connected in parallel with a load fuse in a multi-phase load circuit. The actuators tend to pivot the operator in a common angular direction, whereby the operator may be pivoted into contact with a detector switch.
Background of the invention Current limiting devices such as spring-loaded fuse actuators have been developed for multi-phase circuits, in which one such device is associated with each phase, and all such devices are operatively associated with a common operator element such as a slide, tripper bar, latch, linkage or the like. The operator element is therefore movable by any one of the current limiting devices.
Commonly the fuse actuators or corresponding elements are arranged close together in a line with a common rectilinear direction of motion. This presents a difficulty in higher voltages multi-phase applications where safety or underwriter requirements provide for a minimum over-surface distance between circuit parts connected with different phases. For example, 600 -volt threephase devices normally require two inches over-surface separation between parts connected to different phases. The problem thus presented is to provide a sufiicient surface between the fuse actuators or comp-arable parts without making the device unduly bulky, expensive or unreliable in operation.
Summary The foregoing problem is met, according to the present invention, by means of a vaned pivotal operator element which serves the dual function of a common operator ele ment and an insulating member increasing the effective over-surface distance between the fuse actuators. The vanes extend from the operator in such directions as to form corners and each fuse actuator is situated in one such corner. The vanes are of sufficient size to provide the necessary insulation between the actuators, but undue bulkiness is obviated by distributing the actuators angularly about the insulating operator rather than in a line.
Brief description of the drawing FIG. 1 is a plan view of a preferred embodiment of the invention embodied in a three-phase fuse failure detector;
FIG. 2 is a side elevation corresponding to FIG. 1; and
FIG. 3 is a detail view in section of one of the fuse actuators.
Description of the preferred embodiment Phase lines 12, 14 and 16 extend from a three phase power distribution system to a motor-operated switch 18 that may be opened by energization of a motor M. The load side of this switch has the usual fuses 20, 22 and 24 in position to break the phase lines to a three-phase load 26.
The purpose of the fuse failure detector described below is to open the switch 18 by energization of the motor M when any one or more of the fuses 20, 22 or 24 fails. We turn next to a description of the detector serving this purpose, according to the present invention.
A square base 28 of insulating sheet material, such as a phenolic resin or other suitable plastic, supports all of the operative elements on one side, and it may be provided with holes or edge slots (not shown) for mounting to a suitable enclosure such as a metal fuse or switch enclosure. A pintle 30 having a tapered flat head 32 is supported Within a centrally located countersunk hole in the base 28.
An operator designated generally at 34 is pivotally mounted on the pintle 30, and comprises a square-shaped central block 36 and three vanes 38, 39 and 40 secured to the block by any suitable means such as screws or cement. The vanes are formed of insulating sheet material such as a plastic. The block 36 has a central hole in which are press fitted a pair of flanged sleeves 42 of metal such as bronze, or Teflon, for its bearing. It will be understood that the complete actuating vane assembly could also be made as a one-side moulding of insulating material with proper friction bushings. The sleeves 42 freely pivot about the pintle 30. A retaining washer 44 and cotter pin 46 retain the operator upon the pintle in a conventional manner. There is a slight offset between the operator and the base 28 formed by the flange on the lower sleeve 42.
The vanes provide a plurality of corners Within each of which a fuse actuator is mounted. A fuse actuator 48 is connected in parallel with the load fuse 20, a fuse actuator 50 is in parallel with the load fuse 22, and fuse actuator 52 is in parallel with the load fuse 24. These actuators are of identical construction and are commercially available, and it will suffice to describe briefly here the fuse actuator 48, in connection with FIG. 3.
A pair of mounting clips 54 are screwed to the base 28, and receive the tubular metal ends 56 and 58 of the actuator. These ends are fitted over an insulating tube 60 which is also fitted with an inner metal bearing member 62. A metal cap 64 is received within the member 58. The members 62 and 64 retain the ends of a compression spring 66. An end of the wire forming this spring is soldered at 68 to a fuse wire 70 which is also soldered to the end 56 at 72. The wire forming the spring 66 also has a portion formed into a loop received within a plastic plunger 74. The element 70 normally maintains the spring 66 in compression, and releases the spring when the current is sufficiently high to melt the element. A spring thrust of about one pound is preferred. A plunger thrust of approximately /8 inch ensues as the plunger moves to the position shown in broken lines. It is obvious that the figures given for thrust and displacement are a matter of choice in the design.
The actuators 48, 50 and 52 are placed in mutual right angle relationship so that each delivers the identical torque to the operator 34 in the same angular direction, when it fails. Since the fuse elements 70 of the actuators have a much smaller current capacity than the fuses 20, 22 and 24, if any of the latter fuses should fail, the associated fuse actuator will also fail, releasing its plunger 74 and pivoting the operator 34.
A detector switch 78 having a plunger 80 in contact with the vane 40 is secured to the base 28 by a sheet metal bracket 82. -It Will be apparent from the drawing that counterclockwise rotation of the operator 34 as a result of operation of any one or more of the fuse actu ators 48, 50 or 52 results in depression of the plunger 80 and closure of contacts 84 associated with this plunger in a conventional manner. This closes a circuit connecting a power source with the motor M at a pair of terminals 86, opening the switch 18.
The above-described arrangement of the parts is com.-
pact and easily accessible for servicing and adjustment from a single side of the base 28. The vanes 38, 39 and 40 are so arranged as to provide corners in association with the base 28, whereby theover-surface distance between the fuse actuators, which are at different phase potentials, are adequate to meet strict standards of safety.
It will be apparent that certain modifications in the structure of the device can be accomplished, particularly with regard to the arrangement and position of the switch 7-8. For example, the vane 40 may be shortened to the dimensions of the vanes 38 and 39, and a fourth vane added to thefblock 36 to form a symmetrical operator. In this case the fourth vane may be used to operate t'he switch 78. Also, it is evident that the switch may be arranged for operation either by pushing or pulling the plunger 80, and the contacts 84 may be break contacts instead of the make contacts shown in the drawing. The circuit adaptations associated with such modifications will be evident to one skilled in this art.
It will be understood that other modifications in the structure and in the arrangement of the parts may be accomplished without departing from the spirit or scope of this invention.
Having thus described the invention, I claim:
1. A fuse failure detector for a multi-phase circuit having a plurality of load fuses, said detector having, in combination:
an insulating base, 3
an operator having a pivotal bearing on the base and a plurality of insulating vanes fixed in relation to the bearing and defining a plurality of corners there 4 between, each corner including the base and two vanes,
a plurality of fuse actuators each having a fuse element connected in parallel with a load fuse, mounted on the base in one of said. corners and provided with a plunger and a spring releasable by fusion of the fuse element to propel the plunger, the plungers of the fuse actuators being arranged to pivot the operator in a common angular direction,
and a detector switch mounted on the base in position for .contact by the pivoting operator.
2. The combination according to claim 1, with:
a load switch in the multiphase circuit,
and means connected with a source of power through the detector switch and operable to open the load switch.
3. The combination according to claim 1, in which the part of the operator having the bearing has a plurality of fiat sides and the vanes are sheet members attached to said sides. I
References Cited UNITED STATES PATENTS 825,333 7/1906 Morganthaler 317-46 X 2 ,534,103 12/1950 Camilli 31746 X 3,031,601 4/1962 Rudolph 31746 3,309,478 3/1967 Kiesel et a1 317-46 X LEE T. I-IIX, Primary Examiner. R. V. LUPO Assistant Examiner.
U.S. Cl. X.R.
|Cited Patent||Filing date||Publication date||Applicant||Title|
|US825333 *||Jul 29, 1905||Jul 10, 1906||Gen Electric||Fuse-box.|
|US2534103 *||Sep 24, 1949||Dec 12, 1950||Gen Electric||Three-phase bimetal thermal relay|
|US3031601 *||Sep 27, 1960||Apr 24, 1962||Gen Electric||Circuit protective apparatus|
|US3309478 *||Sep 15, 1965||Mar 14, 1967||Gen Electric||Multi-pole electric circuit breaker and fuse combination with single blownfuse sensing solenoid for all poles|
|Citing Patent||Filing date||Publication date||Applicant||Title|
|US3621431 *||Dec 23, 1969||Nov 16, 1971||Chase Shawmut Co||Blown-fuse indicator including a circuit-controlling switching device|
|US3879696 *||Dec 20, 1973||Apr 22, 1975||Tokyo Shibaura Electric Co||Surge voltage absorber|
|US3889222 *||Nov 7, 1973||Jun 10, 1975||Tokyo Shibaura Electric Co||Surge voltage absorber|
|US3895338 *||Jul 22, 1974||Jul 15, 1975||Gen Electric||Electric fuse with indicating mechanism|
|US4052688 *||Sep 27, 1976||Oct 4, 1977||Bell Telephone Laboratories, Incorporated||Fuse clip assembly|
|US4384266 *||Dec 21, 1981||May 17, 1983||Bell Telephone Laboratories, Incorporated||Fuse apparatus|
|US4799124 *||Oct 31, 1985||Jan 17, 1989||Clairol Incorporated||Shock hazard protector for hair dryers|
|US6323750 *||Apr 20, 1998||Nov 27, 2001||Siemens Matsushita Components Gmbh & Co. Kg||Electrical component with a safety release|
|US8441147 *||Aug 17, 2010||May 14, 2013||Siemens Industry, Inc.||Device and system for bypassing a power cell of a power supply|
|US20100301975 *||Aug 17, 2010||Dec 2, 2010||Siemens Industry, Inc.||Device and system for bypassing a power cell of a power supply|
|U.S. Classification||361/104, 337/244, 337/7|
|International Classification||H01H85/30, H01H85/00|