|Publication number||US5889643 A|
|Application number||US 08/939,263|
|Publication date||Mar 30, 1999|
|Filing date||Sep 29, 1997|
|Priority date||Sep 29, 1997|
|Also published as||CA2248486A1, CA2248486C|
|Publication number||08939263, 939263, US 5889643 A, US 5889643A, US-A-5889643, US5889643 A, US5889643A|
|Inventors||Robert Tracy Elms|
|Original Assignee||Eaton Corporation|
|Export Citation||BiBTeX, EndNote, RefMan|
|Patent Citations (5), Non-Patent Citations (2), Referenced by (94), Classifications (11), Legal Events (4)|
|External Links: USPTO, USPTO Assignment, Espacenet|
1. Field of the Invention
This invention relates to apparatus providing protection in multiwire branch circuits of electric power distribution systems, and in particular, to circuit breakers providing protection from arcing faults and ground faults in such circuits.
2. Background Information
Branch circuits in electric power distribution systems often share a common neutral conductor to reduce the wiring required. Such multiwire branch circuits are often referred to as "home runs." Home runs are permitted as long as the two line conductors are energized by separate phases or by a center tapped single phase to avoid overloading the neutral conductor, and as long as all ungrounded conductors are disconnected simultaneously at the panel board where the branch circuits originate. This simultaneous disconnection of the ungrounded conductors can be accomplished with a two pole disconnect, two single pole circuit breakers with a handle tie, or a two pole circuit breaker.
Presently, such multiwire branch circuits are provided with short circuit and overcurrent protection by the tied single pole breakers or the two pole breaker. Only the two pole breaker can also provide ground fault protection by the addition of a common ground fault detector.
Recently, there has been an increased interest in providing protection from arc faults. Arc faults are intermittent high impedance faults which can be caused for instance by worn insulation, loose connections, broken conductors, and the like. Because of their intermittent and high impedance nature, they do not generate currents of sufficient instantaneous magnitude or sufficient average current to trigger the thermal-magnetic trip device which provides the short circuit and overcurrent protection. Various types of arc fault detectors have been proposed, but to my knowledge they have not been adapted to multiwire branches.
There is a need for a circuit breaker which can provide arc fault protection as well as short circuit and overcurrent, and ground fault protection for multiwire branch circuits.
These needs and others are satisfied by the invention which is directed to an apparatus for detecting faults in multiwire branch circuits. It includes a two pole circuit breaker having a first pole connected to interrupt current in the first line conductor and a second pole connected to interrupt current simultaneously in the second line conductor. The apparatus further includes fault detection circuitry including a first arc fault detector connected to detect arc currents in the first line conductor and to generate a first trip signal in response thereto, a second arc fault detector connected to detect arc currents in the second line conductor and to generate a second trip signal in response thereto, and a ground fault detector connected to detect ground faults between each of the line conductors and ground. The apparatus also includes means responsive to each of the trip signals to trip the two pole circuit breaker. Preferably, the ground fault detector detects neutral to ground faults in addition to line to ground faults. It is also preferred that the ground fault detector have a power supply fed by each of the line conductors so that it remains operative even with one line unpowered.
Preferably, the arc fault detectors utilize the bimetal of the respective pole which is connected in series with the associated line conductor as a known impedance for monitoring the line current. In such an arrangement, the first and second arc fault detectors are referenced to the associated line conductor, and the trip signals are electrically isolated such as by optocouplers from the common trip circuit.
A full understanding of the invention can be gained from the following description of the preferred embodiments when read in conjunction with the accompanying drawings in which:
FIG. 1 is a schematic diagram partly in block form of apparatus in accordance with the invention.
FIG. 2 is a schematic diagram of the arc fault detectors which form part of the apparatus of FIG. 1.
FIG. 3 is a schematic diagram of the ground fault power supply.
FIG. 4 is a schematic diagram of the power supplies for the arc fault detectors.
Referring to FIG. 1, a multiwire branch circuit 1 of an electric power distribution system includes a first line conductor 3, a second line conductor 5 and a common neutral conductor 7. As previously mentioned, the two line conductors 3 and 5 are energized by separate phases, or a center tapped single phase supply voltage. Typically, the neutral conductor is grounded as shown at 9. Protection in this multiwire branch circuit 1 is provided by a two pole circuit breaker 11 which includes separable contacts 131 and 132 connected in series in the line conductors 3 and 5, respectively. Each pole has a thermal-magnetic trip device which includes a bimetal 151 and 152 connected in series in the associated line conductor. The bimetals 15 respond to the heat generated by persistent overcurrent conditions to trip a spring powered operating mechanism (not shown) which is mechanically connected to open both sets of separable contacts 131 and 132 in response to actuation by either trip device. The trip units also include a magnetic actuator (not shown) which actuates the operating mechanism to instantaneously open the contacts 13 in response to very high overcurrents such as those associated with a short circuit.
The two pole circuit breaker 11 is located in a load center (not shown) which provides for distribution of power in various circuits such as the multiwire branch circuit 1. In addition to the instantaneous and delayed overcurrent protection provided by the thermal-magnetic trip devices, the two pole circuit breaker also includes arc fault protection for each of the line conductors 3 and 5 and ground fault protection for all three conductors 3, 5 and 7. Separate arc fault detectors 171 and 172 are provided for the line conductors 3 and 5, respectively. Each of these arc detectors includes a current sensor to detect current in the associated line conductor. In the preferred embodiment of the invention, the bimetal 15 is used as the current sensor. As the low resistance of the bimetal 15 is known, the voltage drop across the bimetal is a measure of the current in the associated line conductor. The voltages across the bimetals are sensed through the leads 191 and 192. Since the arc fault detectors 17 use the associated bimetal 15 as a current sensor, they need to be referenced to the associated line voltage. Accordingly, the Line 1 arc fault detector 171 has a ground 211 referenced to the line conductor 3 while the Line 2 arc fault detector 172 has a ground 212 referenced to the line 2 conductor 5. Each of the arc fault detectors 171 and 172 has its own power supply 231 and 232 connected between the associated line conductor and the neutral conductor 7.
Ground fault protection is provided by the ground fault detector 25. In the preferred embodiment of the invention, the well known dormant oscillator type ground fault detector is employed. A first ground fault detector coil 27 encircles all three of the conductors 3, 5 and 7. In the absence of a ground fault, the resultant current through the coil 27 carried by the three conductors will be zero. A ground fault on either of the line conductors 3 or 5 will create an imbalance in the currents which will be detected by the coil 27. As the neutral conductor 7 is grounded at 9 close to the circuit breaker 11, a ground fault between neutral and ground will not generate a sufficient imbalance in current for the coil 27 to detect. A second coil 29 is used to inject a small voltage into the neutral conductor. If a ground fault is present on the neutral conductor, a loop completed by this ground fault will support an oscillation which will be detected by the ground fault circuitry.
The ground fault detector 25 is powered by a ground fault power supply 31. The ground fault power supply 31 is connected to both of the line conductors 3 and 5 by the leads 331 and 332 so that the ground fault detector 25 is operational if at least one of the line conductors 3 or 5 is energized and the contacts 13 of the circuit breaker are closed. A common lead 35 is connected between the ground fault power supply 31 and the neutral conductor 7. As will be seen, with both line conductors 3 and 5 energized the output voltage of the ground fault supply provided on the lead 37 can be as high as about 300 volts dc. This voltage is used to energize a shunt trip coil 39 which results in the opening of the separable contacts 13 when a silicon controlled rectifier (SCR) 41 is turned on in a manner to be discussed. A circuit 43 draws power from the ground fault power supply 31 through the coil 39 to energize the ground fault detector circuit 25. The current drawn by this power circuit 43 is insufficient to energize the coil to open the contacts 13, but is sufficient to operate the ground fault detector 25. The circuit 43 includes a zener diode 45 which clamps the voltage across a capacitor 47 to about 43 volts. A resistor 49 forms a filter with the capacitor 47 for this 43 volts dc. Another resistor 51 limits the current drawn by the circuit 43 to below the level needed to energize the coil 37 and open the separable contacts 13. The 43 volts dc is applied to the chip implementing the ground fault detector 25 which contains an arrangement of zener diodes represented by the zener diode 53 which generate 26 volts and other voltages needed by the ground fault detector circuit 25. This 26 volt dc is filtered by a capacitor 55.
The Line 1 arc fault detector 171 generates a trip signal on a lead 571 in response to detection of an arc fault on the line 1 conductor 3. Similarly, the Line 2 arc fault detectors 172 generates a trip signal on the lead 572 in response to detection of an arc fault on the line 2 conductor 5. The ground fault detector 25 generates a trip signal on the lead 59 in response to detection of a ground fault between any one of the conductors 3, 5 and 7 and ground. The ground faults detected by the detector 25 can be direct faults to ground or themselves can be arcing faults between a conductor and ground.
A common trip circuit 61 responds to a trip signal generated by any one of the arc fault detectors 171 or 172 or the ground fault detector 25. This common trip circuit 61 includes the SCR 41, which when turned on energizes the trip coil 39 to open the separable contacts 13. As the arc fault detectors 171 and 172 are referenced to the line conductor on which they are providing protection, the three detector circuits must be electrically isolated from one another. This isolation is provided by optocouplers 631 and 632 which convert the trip signals on the leads 571 and 572 to signals on leads 651 and 652 of the common trip circuit 61. Drive current for the optoisolators 631 and 632 is provided from the 26 volt dc supply of the ground fault detector circuit 25 through resistor 67. The leads 651 and 652 from the optoisolators are connected in parallel which each other and with the lead 59 from the ground fault detector 25 to the gate of the SCR 41 so that any one of the three signals can trip the contacts 13 open.
FIG. 2 illustrates a suitable arc fault circuit 171. A similar circuit can be provided for the arc fault circuit 172 keeping in mind that each must be referenced to the line conductor for which it is providing protection since the bimetal in the conductor is being used for current detection. The voltage across the associated bimetal 15 is provided on the leads 191. The arc fault circuit 17 includes a pulse generator 69, a circuit 71 which provides a time attenuated accumulation of the pulses generated by the pulse generator 69, and an output circuit 73 which provides a trip signal on the lead 57.
The pulse generator 69 includes a high pass filter 75 formed by the series connected capacitor 77 and resistor 79, followed by a low pass filter 81 formed by the parallel connected capacitor 83 and resistor 85. The high pass filter 75 and low pass filter 81 have a band pass in a range of about 400 to 590 Hz which generates pulses in response to the step increases in current caused by striking of an arc.
An operational amplifier (op amp) 87 provides gain for the pulses. A capacitor 88 reduces high frequency noise in the pulse signals. The op amp 87 is biased at its non-inverting input by a 13 vdc supply voltage. A resistor 89 and capacitor 91 delay application of the bias to prevent false trip signals during power up. The positive and negative pulses generated by the band pass filter ride on the plus 13 vdc volt bias applied to the op amp 87. This bias is removed by the ac coupling capacitor 93 which along with the resistor 95 forms another high pass filter stage. The bi-polar pulse signal resulting is rectified by a rectifier circuit 97 which includes another op amp 99. Positive pulses are applied to the non-inverting input of the op amp 99 through the diode 101 while negative pulses are applied to the inverting input through the diode 103. The output of the op amp 99 is a pulse signal having pulses of a single polarity.
The circuit 71 generates a time attenuated accumulation of the pulses in the pulse signal generated by the pulse generator 69. The pulses are accumulated on a capacitor 105 connected to the 26 vdc supply. A bleed resistor 107 connected across the capacitor 105 provides the time attenuation. The pulses are applied to the capacitor 105 through a transistor 109. When no pulses are generated, both electrodes of the capacitor 105 are at 26 volts. The pulses from the pulse generator 69 provide base drive current for the transistor 109. A voltage divider formed by the resistor 111 and 113 connected at their common connection to the emitter of the transistor 109 set the minimum amplitude for the pulses to turn on the transistor 109. This threshold is selected so that pulses which could be generated by some normal loads, such as for instance a dimmer switch operating at normal loads, are not accumulated. The amplitude of the pulses is set by the gain of the op amp 99 which in turn is determined by the ratio of the feed back resistor 115 and input resistor 117. The amplitude and duration of each pulse determine the amount of charge which is applied to the capacitor 105. The successive pulses are accumulated through the summation of the charge they add to the capacitor 105. The resistor 107 continuously bleeds the charge on the capacitor 105 with a time constant determined by the values of the capacitor 105 and resistor 107 to time attenuate the accumulation of the pulses. It can be appreciated that the magnitude and time interval between pulses determines the instantaneous voltage that appears across the capacitor 105.
The output circuit 73 monitors the voltage across the capacitor 105 representing the time attenuated accumulation of the pulses in the pulse signal generated by the pulse generator. Each pulse lowers the voltage on the capacitor which is applied to the base of a transistor 119 in the output circuit. A voltage is applied to the emitter of the transistor 119 by the 13 vdc supply through a resistor 121 and diode 123. With no pulses being generated, the voltage on the base of the transistor 119 is 26 volts. Without the diode 123, the 13 volt reverse bias would destroy the base to emitter junction of the transistor 119. The diode 123 withstands this voltage. When the voltage at the lower end of the capacitor 105, and therefore on the base of the transistor 119, falls below the 13 volts minus the forward drop across the diode 123, the transistor 119 is turned on. Feedback provided through the lead 125 and the resistors 127 and 129 holds the transistor 119 on by providing a continuous output of the op amp 99 which holds the transistor 109 on. Turn on of the transistor 119 provides base drive current for the transistor 131 which draws current limited by the resistor 133 to generate an arc fault trip signal on the lead 571. The trip signal actuates the optocoupler 631 which turns on the SCR 41 to trip the separable contacts 13 open. The larger the pulses in the pulse signal generated by the pulse generator 69 the harder the transistor 109 is turned on, and hence, the faster charge is accumulated on the capacitor 105.
A circuit diagram of the ground fault power supply 31 is shown in FIG. 3. This power supply includes a bridge circuit 135 having six diodes 137. Power is supplied to the bridge from the Line 1 conductor 3 through the lead 331 and from the Line 2 conductor 5 through the lead 332. Output of the bridge is between the lead 37 and the ground fault common 139. The lead 331 is connected to the mid-point of one leg of the bridge 135 while the lead 332 is connected to the mid-point of another leg. The neutral conductor 7 is connected to the mid-point of the third leg through the lead 35. A pair of metal oxide varistors (MOVs) 141 protect the power supply 31 from voltage surges on the line conductors. With both line conductors energized the output of the power supply 31 across the lead 37 and common 139 is the line to line voltage. With only one line conductor energized, the output of the power supply 31 is the line to neutral voltage. As can be seen, the potential of the ground fault common 139 changes. When the diode 1371 is conducting, ground fault common 139 is tied to the voltage on Line 1. With the diode 1373 conducting, it is tied to the voltage on Line 2, and if one line is not energized so that diode 1375 conducts on positive half cycles of the line voltage, the ground fault common 139 is tied to neutral.
FIG. 4 illustrates the power supply 231 for the Line 1 arc fault detector 171. This power supply is connected on the hot side to the neutral conductor 7 through the lead 143. The other side of the power supply is connected to the Line 1 conductor 3 through the Line 1 arc fault detector common 211. The diode 145 halfwave rectifies the neutral to Line 1 voltage and the resistor 147 converts this rectified voltage signal to about a 6 milliamp current which charges a capacitor 149. The voltage across capacitor 149 is clamped to 43 volts dc by the zener diode 151. Resistor 153 and capacitor 155 form a second filter. The voltage across the capacitor 155 is clamped at 26 volts dc by the zener diodes 157 and 159 to provide the 26 vdc1 for the Line 1 arc fault detector 171. The common junction between zener diodes 157 and 159 provides the 13 vdc1 supply voltage for arc fault detector 171. The power supply 232 for the Line 2 arc fault detector 172 has a similar circuit configuration except that it is referenced to the common 212.
While specific embodiments of the invention have been described in detail, it will be appreciated by those skilled in the art that various modifications and alternatives to those details could be developed in light of the overall teachings of the disclosure. Accordingly, the particular arrangement disclosed are meant to be illustrative only and not limiting as to the scope of invention which is to be given the full breath of the claims appended and any and all equivalents thereof.
|Cited Patent||Filing date||Publication date||Applicant||Title|
|US5224006 *||Sep 26, 1991||Jun 29, 1993||Westinghouse Electric Corp.||Electronic circuit breaker with protection against sputtering arc faults and ground faults|
|US5307230 *||Aug 26, 1993||Apr 26, 1994||Westinghouse Electric Corp.||Circuit breaker with protection against sputtering arc faults|
|US5459630 *||Sep 15, 1993||Oct 17, 1995||Eaton Corporation||Self testing circuit breaker ground fault and sputtering arc trip unit|
|US5519561 *||Nov 8, 1994||May 21, 1996||Eaton Corporation||Circuit breaker using bimetal of thermal-magnetic trip to sense current|
|US5546266 *||Jun 24, 1994||Aug 13, 1996||Eaton Corporation||Circuit interrupter with cause for trip indication|
|1||*||National Electrical Code Handbook, 1996, Article 210.4 Multiwire Branch Circuits , pp. 54 55.|
|2||National Electrical Code Handbook, 1996, Article 210.4 Multiwire Branch Circuits, pp. 54-55.|
|Citing Patent||Filing date||Publication date||Applicant||Title|
|US6014297 *||Mar 16, 1999||Jan 11, 2000||Eaton Corporation||Apparatus for detecting arcing faults and ground faults in multiwire branch electric power circuits|
|US6141192 *||Nov 12, 1998||Oct 31, 2000||Square D Company||Arcing fault protection system for a switchgear enclosure|
|US6218844||Dec 16, 1998||Apr 17, 2001||Square D Company||Method and apparatus for testing an arcing fault circuit interrupter|
|US6242993||Feb 6, 1997||Jun 5, 2001||Square D Company||Apparatus for use in arcing fault detection systems|
|US6246556||Feb 19, 1998||Jun 12, 2001||Square D Company||Electrical fault detection system|
|US6259996||Aug 5, 1998||Jul 10, 2001||Square D Company||Arc fault detection system|
|US6275044 *||Jul 15, 1998||Aug 14, 2001||Square D Company||Arcing fault detection system|
|US6313641||Jul 1, 1999||Nov 6, 2001||Square D Company||Method and system for detecting arcing faults and testing such system|
|US6377427||Dec 17, 1999||Apr 23, 2002||Square D Company||Arc fault protected electrical receptacle|
|US6477021||Dec 21, 1999||Nov 5, 2002||Square D Company||Blocking/inhibiting operation in an arc fault detection system|
|US6532140||Jun 2, 2000||Mar 11, 2003||Raytheon Company||Arc-fault detecting circuit breaker system|
|US6532424||Apr 11, 2000||Mar 11, 2003||Square D Company||Electrical fault detection circuit with dual-mode power supply|
|US6567250||Dec 22, 1999||May 20, 2003||Square D Company||Arc fault protected device|
|US6577138 *||Aug 24, 2001||Jun 10, 2003||Eaton Corporation||Apparatus for detecting arcing and overcurrents in dc electrical systems subject to cyclic disturbances|
|US6591482||Nov 17, 2000||Jul 15, 2003||Square D Company||Assembly methods for miniature circuit breakers with electronics|
|US6621669||Dec 17, 1999||Sep 16, 2003||Square D Company||Arc fault receptacle with a feed-through connection|
|US6625550||Oct 26, 1999||Sep 23, 2003||Square D Company||Arc fault detection for aircraft|
|US6707651||Jun 3, 2002||Mar 16, 2004||Eaton Corporation||ARC fault or ground fault or ARC fault/ground fault trip signal generator and trip unit employing the same|
|US6707652||Jul 10, 2002||Mar 16, 2004||Eaton Corporation||Electrical switching apparatus including glowing contact protection|
|US6717786||Oct 30, 2001||Apr 6, 2004||The Boeing Company||Automatic voltage source selector for circuit breakers utilizing electronics|
|US6720872||Jul 16, 2002||Apr 13, 2004||Eaton Corporation||Ground fault/arc fault circuit interrupter and method of testing the same with a test button and a reset button|
|US6738241||Mar 27, 2002||May 18, 2004||Tower Manufacturing Corporation||Fireguard circuit|
|US6782329 *||Jan 17, 2001||Aug 24, 2004||Square D Company||Detection of arcing faults using bifurcated wiring system|
|US6948846||Oct 23, 2003||Sep 27, 2005||Eaton Corporation||Test apparatus for power circuits of an electrical distribution device|
|US6961226||Nov 12, 2002||Nov 1, 2005||General Electric Company||Method and system for providing power to circuit breakers|
|US6972936 *||Mar 29, 2002||Dec 6, 2005||Robert Allan Morris||Pre-emptive circuit breaker with arc fault and fault lockout short circuit protection|
|US7035066||Dec 23, 2002||Apr 25, 2006||Raytheon Company||Arc-default detecting circuit breaker system|
|US7149066||Oct 7, 2003||Dec 12, 2006||Eaton Corporation||Fault detector for two line power distribution system and protection apparatus incorporating the same|
|US7423854||Jul 7, 2006||Sep 9, 2008||Technology Research Corporation||Interruption circuit with improved shield|
|US7460346||Sep 15, 2005||Dec 2, 2008||Honeywell International Inc.||Arc fault detection and confirmation using voltage and current analysis|
|US7508096||Sep 20, 2007||Mar 24, 2009||General Electric Company||Switching circuit apparatus having a series conduction path for servicing a load and switching method|
|US7525777||Jul 7, 2004||Apr 28, 2009||Tower Manufacturing Corporation||Fireguard circuit|
|US7546214||Jun 8, 2007||Jun 9, 2009||General Electric Company||System for power sub-metering|
|US7554222||Nov 1, 2007||Jun 30, 2009||General Electric Company||Micro-electromechanical system based switching|
|US7589942||Jun 15, 2007||Sep 15, 2009||General Electric Company||MEMS based motor starter with motor failure detection|
|US7612971||Nov 3, 2009||General Electric Company||Micro-electromechanical system based switching in heating-ventilation-air-conditioning systems|
|US7623329||Jul 7, 2006||Nov 24, 2009||Technology Research Corporation||Leakage current detection and interruption circuit with improved shield|
|US7626796 *||Apr 18, 2007||Dec 1, 2009||Leviton Manufacturing Co., Inc.||Power distribution unit with two pole circuit breaker|
|US7633399||Feb 27, 2007||Dec 15, 2009||Eaton Corporation||Configurable arc fault or ground fault circuit interrupter and method|
|US7719257||Jun 7, 2007||May 18, 2010||General Electric Company||Current sensing module and assembly method thereof|
|US7751161||Jul 6, 2010||Technology Research Corporation||Leakage current detection and interruption circuit|
|US7839611||Nov 23, 2010||General Electric Company||Programmable logic controller having micro-electromechanical system based switching|
|US7885043||Feb 8, 2011||General Electric Company||Remote-operable micro-electromechanical system based over-current protection apparatus|
|US7903382||Mar 8, 2011||General Electric Company||MEMS micro-switch array based on current limiting enabled circuit interrupting apparatus|
|US7924541||Apr 12, 2011||Long Zhang||Power plug with leakage current protection function|
|US7944654||Nov 10, 2008||May 17, 2011||Scott Gary W||Multiple-pole circuit breaker with shared current sensor for arcing fault detection|
|US7944660||May 17, 2011||General Electric Company||Micro-electromechanical system based selectively coordinated protection systems and methods for electrical distribution|
|US8064174||Aug 11, 2009||Nov 22, 2011||Technology Research Corporation||Leakage current detection and interruption circuit with improved shield|
|US8072723||Jun 19, 2007||Dec 6, 2011||General Electric Company||Resettable MEMS micro-switch array based on current limiting apparatus|
|US8144445||Jun 12, 2007||Mar 27, 2012||General Electric Company||Micro-electromechanical system based switching|
|US8358488||Jun 15, 2007||Jan 22, 2013||General Electric Company||Micro-electromechanical system based switching|
|US8659857||Jul 23, 2009||Feb 25, 2014||Technology Reasearch Corporation||Leakage current detection and interruption circuit powered by leakage current|
|US8810983||Dec 4, 2009||Aug 19, 2014||Asco Power Technologies, L.P.||Power disconnect system and method|
|US8884638 *||Sep 24, 2008||Nov 11, 2014||Continental Automotive Gmbh||Circuit arrangement for monitoring an electrical insulation|
|US9349559 *||Mar 22, 2010||May 24, 2016||Siemens Industry, Inc.||Low-profile electronic circuit breakers, breaker tripping mechanisms, and systems and methods of using same|
|US20010029433 *||Jan 17, 2001||Oct 11, 2001||Scott Gary W.||Detection of arcing faults using bifurcated wiring system|
|US20030184931 *||Mar 29, 2002||Oct 2, 2003||Morris Robert Allan||Pre-emptive circuit breaker with arc fault and fault lockout short circuit protection|
|US20040042137 *||May 13, 2003||Mar 4, 2004||Wong Kon B.||Load recognition and series arc detection using bandpass filter signatures|
|US20040090723 *||Nov 12, 2002||May 13, 2004||Mason Henry Hall||Method and system for providing power to circuit breakers|
|US20040228048 *||Feb 20, 2004||Nov 18, 2004||Aromin Victor V.||Fireguard circuit|
|US20050013069 *||May 13, 2004||Jan 20, 2005||Aromin Victor V.||Fireguard circuit|
|US20050073780 *||Oct 7, 2003||Apr 7, 2005||Elms Robert T.||Fault detector for two line power distribution system and protection apparatus incorporating the same|
|US20050089079 *||Oct 23, 2003||Apr 28, 2005||Engel Joseph C.||Test apparatus for power circuits of an electrical distribution device|
|US20060061924 *||Jun 29, 2005||Mar 23, 2006||Shanghai Ele Manufacturing Corp.||Power plug with leakage current protection function|
|US20060146456 *||Dec 30, 2005||Jul 6, 2006||Technology Research Corporation||Leakage current detection and interruption circuit|
|US20060203402 *||Feb 21, 2006||Sep 14, 2006||Aromin Victor V||Fireguard circuit|
|US20060215335 *||Sep 15, 2005||Sep 28, 2006||Honeywell International Inc.||Arc fault detection and confirmation using voltage and current analysis|
|US20070132531 *||Dec 14, 2005||Jun 14, 2007||Eaton Corporation||Two pole circuit interrupter employing a single arc fault or ground fault trip circuit|
|US20070159740 *||Jul 7, 2006||Jul 12, 2007||Technology Research Corporation||Leakage current detection and interruption circuit with improved shield|
|US20080079437 *||Jun 7, 2007||Apr 3, 2008||General Electric Company||Current Sensing Module and Assembly Method Thereof|
|US20080082276 *||Jun 8, 2007||Apr 3, 2008||Cecil Rivers||System for power sub-metering|
|US20080259533 *||Apr 18, 2007||Oct 23, 2008||Leviton Manufacturing Co., Inc.||Power distribution unit with two pole circuit breaker|
|US20080308254 *||Jun 15, 2007||Dec 18, 2008||General Electric Company||Micro-electromechanical system based switching in heating-ventilation-air-conditioning systems|
|US20080308394 *||Jun 15, 2007||Dec 18, 2008||General Electric Company||Micro-electromechanical system based switching|
|US20080309438 *||Jun 12, 2007||Dec 18, 2008||General Electric Company||Micro-electromechanical system based switching|
|US20080310056 *||Jun 15, 2007||Dec 18, 2008||General Electric Company||Remote-operable micro-electromechanical system based over-current protection apparatus|
|US20080310057 *||Jun 15, 2007||Dec 18, 2008||General Electric Company||Mems based motor starter with motor failure detection|
|US20080310058 *||Jun 15, 2007||Dec 18, 2008||General Electric Company||Mems micro-switch array based current limiting arc-flash eliminator|
|US20080310062 *||Jun 15, 2007||Dec 18, 2008||General Electric Company||Micro-electromechanical system based selectively coordinated protection systems and methods for electrical distribution|
|US20080315980 *||Jun 19, 2007||Dec 25, 2008||General Electric Company||Mems micro-switch array based on current limiting enabled circuit interrupting apparatus|
|US20080316664 *||Jun 19, 2007||Dec 25, 2008||General Electric Company||Resettable mems micro-switch array based on current limiting apparatus|
|US20090079273 *||Sep 20, 2007||Mar 26, 2009||General Electric Company||Switching circuit apparatus having a series conduction path for servicing a load and switching method|
|US20090115255 *||Nov 1, 2007||May 7, 2009||General Electric Company||Micro-electromechanical system based switching|
|US20090125124 *||Nov 14, 2007||May 14, 2009||General Electric Company||Programmable logic controller having micro-electromechanical system based switching|
|US20090303642 *||Aug 11, 2009||Dec 10, 2009||Technology Research Corporation||Leakage current detection and interruption circuit with improved shield|
|US20100020452 *||Jul 23, 2009||Jan 28, 2010||Technology Research Corporation||Leakage current detection and interruption circuit powered by leakage current|
|US20100118451 *||Nov 10, 2008||May 13, 2010||Square D Company||Multiple-pole circuit breaker with shared current sensor for arcing fault detection|
|US20100238611 *||Sep 23, 2010||Siemens Industry, Inc.||Low-profile electronic circuit breakers, breaker tripping mechanisms, and systems and methods of using same|
|US20100254053 *||Dec 4, 2009||Oct 7, 2010||Emerson Electric Co.||Power disconnect system and method|
|US20100308841 *||Sep 24, 2008||Dec 9, 2010||Continental Automotive Gmbh||Circuit arrangement for monitoring an electrical insulation|
|US20140307353 *||Sep 24, 2013||Oct 16, 2014||Eaton Corporation||Power system including a load panel protecting a facility from a broken or missing neutral of a split phase electrical distribution configuration|
|US20150049420 *||Aug 19, 2013||Feb 19, 2015||Siemens Industry, Inc.||Low-profile electronic circuit breakers, systems, and methods|
|CN101556301B||Apr 7, 2009||Jul 17, 2013||西门子工业公司||多功能住宅电路断路器|
|CN104034991A *||Mar 4, 2013||Sep 10, 2014||益而益(集团)有限公司||Ground fault detection and resetting apparatus|
|U.S. Classification||361/42, 361/115, 361/45|
|International Classification||H02H3/10, H02H1/00, H02H3/05|
|Cooperative Classification||H02H1/0038, H02H3/05, H02H1/0015, H02H3/105|
|Sep 29, 1997||AS||Assignment|
Owner name: EATON CORPORATION, OHIO
Free format text: ASSIGNMENT OF ASSIGNORS INTEREST;ASSIGNOR:ELMS, ROBERT TRACY;REEL/FRAME:008834/0779
Effective date: 19970923
|Aug 29, 2002||FPAY||Fee payment|
Year of fee payment: 4
|Aug 23, 2006||FPAY||Fee payment|
Year of fee payment: 8
|Aug 24, 2010||FPAY||Fee payment|
Year of fee payment: 12