|Publication number||US6927562 B2|
|Application number||US 10/171,263|
|Publication date||Aug 9, 2005|
|Filing date||Jun 13, 2002|
|Priority date||Feb 27, 2002|
|Also published as||US20030160602|
|Publication number||10171263, 171263, US 6927562 B2, US 6927562B2, US-B2-6927562, US6927562 B2, US6927562B2|
|Inventors||Ramesh Anand, Jeffrey D. Benach, Emidio Cimini, Jan C. Heyneke|
|Original Assignee||On-Line Monitoring, Inc.|
|Export Citation||BiBTeX, EndNote, RefMan|
|Patent Citations (16), Non-Patent Citations (1), Referenced by (12), Classifications (9), Legal Events (13)|
|External Links: USPTO, USPTO Assignment, Espacenet|
Priority is claimed herein to U.S. Provisional Application No. 60/359,908, filed Feb. 27, 2002, which is incorporated by reference herein.
The present invention relates to a system for permitting the testing of power and current transformers and circuit breakers and other high voltage equipment while they are still on line at high voltage. More specifically, the present invention relates to a system for measurement of power factor (also known as the “dielectric loss angle” or “dissipation factor”) to enable diagnosis of the condition of high power stand off insulators.
There are well established techniques for testing deterioration of high voltage (HV) equipment, and specifically the insulators of that equipment. Such methods involve first disconnecting the equipment from the HV line. The purpose of disconnecting the equipment is to avoid the substantial danger to personnel and/or testing equipment that is connected to high power equipment. In practice, it has been very expensive to disconnect equipment for testing. In addition to the man-power required to disconnect the HV equipment, connect it to test equipment and perform the test, the service of the equipment is lost for whatever period of time it takes to disconnect, make the test and reconnect. If there are large numbers of transformers and circuit breakers, and other equipment to be tested, the shut-down can be lengthy and the loss of revenue to the power company very substantial.
Testing the condition of insulation in HV equipment is an essential task. The insulation which is most subject to deterioration is contained within the HV standoff insulator and includes oilpaper insulation and a metallic foil or, alternatively, a conductive coating on the paper wrapped in a roll around the HV conductor at the center of the insulator. The insulating oil which surrounds the transformer, or other HV device, within the grounded metallic casing extends into contact with and saturates the oilpaper to improve its insulation properties. Deterioration usually occurs in the paper or metal foil or coating. Age and temperature contribute to such deterioration, particularly hot spots which may ultimately burn the paper. The actual time of deterioration can vary considerably and, therefore many power companies adopt a schedule of offline testing. The standard testing for insulator deterioration is widely known as Power Factor or Tan/δ testing to determine when power factor of an insulator has reached a dangerous condition and the insulation should be replaced. Normal aging of HV equipment is a slow process that can take place over 30 to 40 years due to thermal, electrical and environmental effects. Premature failure on the other hand is often a relatively sudden process that is not anticipated by periodic off-line tests. Failure to detect insulation deterioration can result in disastrous consequences, ultimately causing heating of the equipment, fire and explosion. Heat may generate various hydrocarbon gases from the oil used in the transformer and some of these gases, such as acetylene, are highly flammable and may be explosive. Pressure builds up and gases are eventually ignited when fire occurs or heating becomes extremely severe so as to initiate a spontaneous combustion. The resulting explosion shatters porcelain insulators and sends pieces flying, damaging adjacent equipment. In a sub-station, or other areas where multiple sets of equipment are employed, an explosion not only results in loss of the exploded device, but also may result in damage to other very expensive equipment, as well as posing substantial danger to personnel working in the area, or even to passers-by in some locations.
The eventual breakdown of insulation is a rapid avalanche of failing dielectric layers. Damaged or deteriorated dielectric is associated with the following: 1) Increased dielectric losses (I2R) with other sources of heating may eventually fuel a mechanism of thermal runaway. PF is a measure of dielectric losses. 2) Partial discharges and treeing. High levels of partial discharge are reflected in the PF and are usually only present just after lightning or switching impulses and just before and during insulation failure. 3) Increased sensitivity to changes in temperature, humidity, and moisture (i.e., increased temperature coefficient). Sources of heating include dielectric losses, ambient temperature, and more significantly, load fluctuations. Most power companies are faced with the dilemma of taking equipment offline and testing it with consequent loss of revenue to the company, or, alternatively, leaving the equipment online without testing longer than it should be. The latter course allows damage to occur and take its toll. Therefore, there has existed for many years a need for a safe means of frequently periodically testing transformer and circuit-breaker bushing insulators without taking the equipment offline. The present invention is directed to such a means, which include a system and a process for testing the equipment and accumulating data about the condition of insulation without taking the equipment offline.
In accordance with the present invention, there is provided a test system, including a coupling means which provides a capacitive voltage divider to obtain a low potential signal proportionate to the HV across a bushing standoff insulator which can be continually measured. To provide a capacitive voltage divider, a tap to the conductor within the oilpaper insulator must be made intermediate to the HV conductor and ground. The conductor as mentioned may be a metal foil or a conductive coating on one side of the oilpaper insulator. Such a coating may be applied before the paper is oiled and be composed, for example, of particulate conductive material in a binder applied by painting or spraying onto one side of the paper before it is rolled up. If the conductor is a foil it may be a continuous wide strip rolled up with the paper. A tap conductively engaging the metallic layer near the grounded end remote from the HV terminal may be provided for various purposes. In some cases the tap is brought outside the bushing to a terminal supported on the outside of the bushing insulator. The tap's low voltage will be proportional to the HV and follow variations in the HV. If no terminal exists outside the bushing, one may be provided by passing a low voltage connection through the porcelain insulator of the bushing at its low voltage bottom end. A bushing tap coupler supported on the outside of the bushing connects to a conductive lead through the bushing to circuitry in the coupler and circuitry within the Interface Cabinet to provide the voltage divider and protection circuitry.
Electrically connected through the coupler to the reduced voltage tap and to the ground end of the insulator is a voltage reduction circuit in the Interface Cabinet which also completes the voltage divider. The voltage reduction circuit includes a series choke coil and parallel capacitors which feed a transformer which reduces the voltage at the secondary winding. Output leads from the secondary, across which may be provided capacitor and solid state bypass means, are connected to computer connection terminals.
Similar circuits are provided for input from each of the insulators in the equipment under test preferably in a single, grounded interface cabinet. For example, a three-phase system is provided with three similar circuits measuring outputs from the three different insulators of the same equipment. Alternatively, three separate insulators on single phase equipment can be connected to the three separate voltage reduction circuits. The interface cabinet is waterproof and permanently installed on or near the equipment subject to test so that it is always available for test.
A computer connects to a mating connector for each of the output leads of the voltage reduction circuits. The software provided is installed in a users PC and programmed to input through an analog to digital converter for each circuit to produce a digital signal which is then processed by a software program providing a Fourier analysis processor to obtain a power factor value. The power factor (PF) calculation in PF Live software is based on the conventional Schering Bridge. Data is acquired under software control from transducers connected to the test objects associated with a transformer and then the data is compared to data from another electrical phase to produce a power factor value. Each power factor reading for each insulator is coordinated with test data and equipment identification and location information. All this coordinated data can be stored on demand by the computer, in a preselected tabular form with power factor calculations from other insulators in the same equipment tested and identified placed in a common table, for example, and separate tables, or other related arrangements for keeping coordinated data on other equipment of the same sub-station. This calculation of a particular date of testing may be displayed, printed out together and/or stored so that the results may be compared from the same insulator from time-to-time based on relatively frequent checks of the system. A comparison table for each insulator showing dates of testing and power factor readings for each date can be compiled. Based on experience, it can be determined that when there are changes in the output amounting to a predetermined amount of change, it is time to disconnect a unit of equipment and proceed with the traditional offline full power factor check to be sure that the equipment is truly ready for insulator replacement. Meantime, however, the equipment has remained in service without interruption usually for years with consequent savings by avoiding large scale maintenance tests and loss of income from sales of power which otherwise have been unavailable to customers during shutdown.
A coupler is provided to a capacitive voltage divider including the effective low voltage capacitance load across the part of the conductive layers wrapped in insulating material connected to a tap at a low voltage point on the conductor wrapped within the insulator structure and providing an external connector to the tap coupler divider circuit. An external connection to the ground is also provided for the voltage divider. A voltage reduction circuit is connected to the external low voltage and ground output connections of the coupler. The voltage reduction circuit completes the voltage divider and further reduces the voltage in the voltage reduction circuit is to provide at the output terminals voltage levels suitable for connection to a computer and providing an output terminal for connecting to other components as desired. The computer is connectable to the output terminals of the voltage reduction circuit and contains software to convert a received analog signal to digital and subjecting the digital signal to a Fourier analysis to produce an output signal representative of power factor.
The invention also provides a method of measuring power factor of a bushing insulator of the type described above in high power (HP) electrical equipment. It first requires disconnecting high power from the equipment to initially install the coupler. Then the method requires providing a low voltage connection to a conductive capacitive layer at the low voltage end of the insulation roll around the HV center conductor in a bushing. This enables forming a capacitive voltage divider with a bushing tap coupler to provide voltage output from the coupler on the order of household voltage when HV is reconnected to the equipment. Then the method requires connecting the low voltage at the output of the coupler and voltage divider to a voltage reduction circuit to complete the voltage divider and produce a voltage level acceptable to a computer. Next, HV is reconnected to the equipment, so that the computer voltage is available on demand at the output to measurement equipment. Then a computer connectable to the further reduced voltage output of the voltage divider with a Fourier analysis program is provided for calculating power factor. The computer recalculates, processes and stores the bushing insulator power factor at periodic intervals.
The present invention also relates to a method of testing HV insulators for HV power equipment from which a low voltage output has been provided across a capacitive voltage divider from a tap to a conductive capacitive layer at the low voltage end of the insulation roll around a HV center conductor in a bushing and is made accessible through a bushing tap coupler. A voltage reduction circuit to reduce the voltage is then connected across the low voltage obtained from the voltage divider to achieve a level acceptable to a computer. A computer is provided with programming to provide a suitable input signal to a Fourier analysis program to obtain the power factor of the insulator. The computer is connected to the voltage reduction circuit to obtain a reading of power factor of that insulator to store in memory with an indication of date and place and with identification of the specific insulator on the specific equipment tested.
For a better understanding of the present invention reference is made to the accompanying drawings in which,
In accordance with the present invention, a low voltage is taken off a bushing tap. That voltage may advantageously be on the order of household voltage 110 volts ac. In
The output from the bushing tap coupler 24C as previously mentioned is an output from connector 26 c providing approximately 110 volts or some other selected voltage in that approximate range. That voltage is fed into the PF Live interface cabinet 28 through a choke coil 38 and a fuse 40 to the primary 42 a which has a capacitor 44, and probably multiple capacitors, across its input. It also has a spark gap 46 across its input. The interface cabinet 28 is primarily provided to reduce the voltage to one suitable input to a laptop computer 32 and that voltage is output across the secondary 42 b on input lead 30 c and an Analog ground connection. Preferably quick connectors are provided which allow the laptop or other computer to be quickly plugged in on site, of course, with no interruption of power. The quick connect plug may include connectors for all three phases. The computer 32 is advantageously a laptop for portability and requires an analog to digital converter module and an analysis program based on a Fast Fourier transform algorithm, as described below, for deriving the power factor from the signals input from each of the phases.
While the voltage acceptable to computers is relatively low, the invention might have applications for higher voltage. There are a number of international standards for what is a safe voltage level, and there may be various applications of the invention requiring voltage higher than 5 volts. Any such useful voltage is intended to be included as possible, provided it is safe to the user. Such voltage is defined in IEG 61010-1 (Second Edition 2001-02), published as a “Group Safety Publication” by IEC as the International Standard. In paragraph 6.3, Permissible Limits for Accessible Parts, and its subparagraphs 6.3.1, Values in Normal Condition, and 6.3.3, Values in Single Fault Condition, give boundaries to safe voltages.
The power factor (PF) measurement is based on the derivation of the phase shift between two voltage signals. For signals consisting of sequences of samples xi and yi the phase angle is preferably determined by first utilizing a Fast Fourier Transform formula to obtain sine and cosine components of the the signals as follows:
where a is the cosine component of signal xi, b is the sine component of signal xi, and n is the number of samples per channel utilized for each measurement. After having obtained sine and cosine components (ax, bx), (ay, by) for the respective x and y channels, tan(δ) is determined as:
The value of δ thus obtained is preferably corrected for error induced by sampling by subtracting (2π[system frequency]/[sampling rate]). The relative power factor is then given as PF=cos((π/2)−δ).
The measurement of PF of insulation is accepted as part of well-established laboratory testing procedures to determine the quality of insulation at the factory before commissioning new and refurbished HV equipment. PF as a parameter is by nature a relatively slow-changing value and is an integral characteristic depending on: 1) Design, materials and production technology; 2) Operating voltages and temperatures; 3) Aging of insulation related to design and operating conditions such as over-voltages, loading conditions, etc.; and 4) Climatic/Weather related Phenomenon.
The system calculates the PF of a unit as a relative value compared with a reference voltage from another device that is in service, thereby eliminating the need for a standard capacitor. The reference device does not have to be associated with the same phase since the system of the present invention is configured to automatically make the proper phase angle adjustments. Relative measurements and evaluation can reduce the affect of influences such as ambient temperature, operating voltages, loading conditions, different aging characteristics, different designs, operating conditions, etc.
The software permits entering the nameplate PF values for each sample under test. Using this value, the PF is normalized to a PF result, which is comparable to an off-line test value.
An output stored in a memory database which identifies each piece of apparatus in each substation or other instalation having insulators checked, specifically identifies specific insulators of each piece of equipment and the test results at a particular date of testing. It is also advantageous to provide a trending program developed for analyzing the readings of a particular type of insulator over time and based upon experience determining when that insulator is becoming sufficiently doubtful because of its change in calculated power factor to justify full testing, i.e., removing the equipment from HV and checking the insulator with more precise equipment known in the art. The data is stored in memory including the calculated power factors (PF) for each insulator together with dates of tests may be displayed on the screen of the laptop or the laptop may be plugged into a larger screen for better facilities for viewing. The results of course can be displayed, printed out or handled in other conventional ways that data is accessed from computers.
The PF Live software in its present form executes on a notebook computer, having the following components: Windows 95, 98, Me, NT4 or 2000, Pentium II 233 MHz processor, CD Rom Drive, 64 MB RAM, 50 MB Hard drive space available for data storage, and 1 available Class 1 PCMCIA slot. Modified software may be used or computers having somewhat different capabilities.
|Cited Patent||Filing date||Publication date||Applicant||Title|
|US4419619 *||Sep 18, 1981||Dec 6, 1983||Mcgraw-Edison Company||Microprocessor controlled voltage regulating transformer|
|US4757263 *||May 1, 1987||Jul 12, 1988||Tennessee Valley Authority||Insulation power factor alarm monitor|
|US4801937 *||Jun 16, 1986||Jan 31, 1989||Fernandes Roosevelt A||Line mounted apparatus for remote measurement of power system or environmental parameters beyond line-of-site distanc|
|US5303164 *||Nov 12, 1991||Apr 12, 1994||Merlin Gerin||Insulation monitor with improved precision|
|US5539655 *||Mar 23, 1994||Jul 23, 1996||Kabushiki Kaisha Toshiba||Apparatus for detecting out of phase of power systems and method for detecting the same|
|US5640154 *||Aug 22, 1995||Jun 17, 1997||Square D Company||Insulation monitoring system for insulated high voltage apparatus|
|US5652521 *||Dec 19, 1995||Jul 29, 1997||Square D Company||Insulation monitoring system for insulated high voltage apparatus|
|US6028430 *||Nov 24, 1997||Feb 22, 2000||Hsp Hochspannungsgeraete Porz Gmbh||Method for monitoring a capacitor bushing, and monitoring system|
|US6141230 *||Jul 13, 1998||Oct 31, 2000||Broadband Telcom Power, Inc.||Valley-fill power factor correction circuit|
|US6177803 *||Jun 7, 1995||Jan 23, 2001||Doble Engineering Company||Monitoring elements in a multi-phase alternating current network|
|US6433557 *||Dec 21, 2000||Aug 13, 2002||Eaton Corporation||Electrical system with capacitance tap and sensor for on-line monitoring the state of high-voltage insulation and remote monitoring device|
|US20020074156 *||Dec 14, 2001||Jun 20, 2002||Mechanical Dynamics And Analysis, Llc||High voltage bushing and method of assembling same|
|US20020079903 *||Dec 21, 2000||Jun 27, 2002||Smith James E.||Electrical system with a stress shield system for partial discharge on-line monitoring of the state of high-voltage insulation|
|US20020079906 *||Dec 21, 2000||Jun 27, 2002||Rashkes Viktor S.||Electrical system with capacitance tap and sensor for on-line monitoring the state of high-voltage insulation and remote monitoring device|
|US20040046531 *||Nov 19, 2001||Mar 11, 2004||Vincenzo Ferraro||System for correcting power factor and harmonics present on an electroduct in an active way and with high-dynamics|
|JPH09182294A *||Title not available|
|1||*||CEI/IEC 61010-1 (second edition 2001-2), pp. 1,3,5-6,9,19,39,43,45,61,65,67.|
|Citing Patent||Filing date||Publication date||Applicant||Title|
|US8466690 *||May 9, 2006||Jun 18, 2013||University Court Of Glasgow Caledonian University||High voltage insulation monitoring sensor|
|US9035659||Jun 22, 2011||May 19, 2015||Techimp Hq S.R.L.||Apparatus and method for measuring the dissipation factor of an insulator|
|US9110117||Apr 16, 2010||Aug 18, 2015||Avo Multi-Amp Corporation||System and method for detecting voltage dependence in insulation systems based on harmonic analysis|
|US9234926||Jun 22, 2011||Jan 12, 2016||Techimp Hq S.R.L.||Apparatus and method for measuring the dissipation factor of an insulator|
|US9482699 *||Jun 12, 2014||Nov 1, 2016||Advanced Power Technologies, Llc||Method and apparatus for monitoring high voltage bushings safely|
|US20080309351 *||May 9, 2006||Dec 18, 2008||University Court Of Glasgow Caledonian Universily||High Voltage Insulation Monitoring Sensor|
|US20140368215 *||Jun 12, 2014||Dec 18, 2014||Gary R Hoffman||Method and apparatus for monitoring high voltage bushings safely|
|US20160202303 *||Jan 9, 2015||Jul 14, 2016||General Electric Company||Use of voltage probe to measure high voltage amplitude and phase to improve on-line bushing monitoring relevance|
|CN103760423A *||Jan 8, 2014||Apr 30, 2014||国家电网公司||Method for measuring inter-phase mutual capacitances of long-distance extra-high voltage double-circuit lines on same tower|
|CN103760423B *||Jan 8, 2014||Mar 2, 2016||国家电网公司||一种长距离特高压同塔双回线路相间互电容测量方法|
|WO2012001585A1||Jun 22, 2011||Jan 5, 2012||Techimp Technologies S.R.L.||Apparatus and method for measuring the dissipation factor of an insulator|
|WO2012001586A1||Jun 22, 2011||Jan 5, 2012||Techimp Technologies S.R.L.||Apparatus and method for measuring the dissipation factor of an insulator|
|U.S. Classification||324/126, 324/551|
|International Classification||G01R31/327, G01R27/26|
|Cooperative Classification||G01R31/3272, G01R31/3271, G01R27/2688|
|European Classification||G01R27/26E, G01R31/327B|
|Jun 13, 2002||AS||Assignment|
Owner name: AVO INTERNATIONAL, NEVADA
Free format text: ASSIGNMENT OF ASSIGNORS INTEREST;ASSIGNORS:ANAND, RAMESH K.;BENACH, JEFFREY D.;CIMINI, EMIDIO;AND OTHERS;REEL/FRAME:013017/0577
Effective date: 20020606
|Apr 30, 2003||AS||Assignment|
Owner name: ON-LINE MONITORING, INC., PENNSYLVANIA
Free format text: ASSIGNMENT OF ASSIGNORS INTEREST;ASSIGNOR:AVO INTERNATIONAL, INC.;REEL/FRAME:014013/0154
Effective date: 20030401
|Feb 16, 2009||REMI||Maintenance fee reminder mailed|
|Aug 9, 2009||REIN||Reinstatement after maintenance fee payment confirmed|
|Sep 29, 2009||FP||Expired due to failure to pay maintenance fee|
Effective date: 20090809
|Oct 25, 2010||PRDP||Patent reinstated due to the acceptance of a late maintenance fee|
Effective date: 20101027
|Oct 27, 2010||FPAY||Fee payment|
Year of fee payment: 4
|Oct 27, 2010||SULP||Surcharge for late payment|
|Nov 9, 2010||AS||Assignment|
Owner name: GRIDSENSE INC., PENNSYLVANIA
Free format text: ASSIGNMENT OF ASSIGNORS INTEREST;ASSIGNOR:ON-LINE MONITORING, INC.;REEL/FRAME:025416/0590
Effective date: 20101105
|Jan 18, 2013||FPAY||Fee payment|
Year of fee payment: 8
|Dec 20, 2013||AS||Assignment|
Owner name: WEIDMANN DIAGNOSTIC SOLUTIONS INC., MASSACHUSETTS
Free format text: ASSIGNMENT OF ASSIGNORS INTEREST;ASSIGNOR:GRIDSENSE, INC.;REEL/FRAME:031828/0201
Effective date: 20131203
|Jan 28, 2015||AS||Assignment|
Owner name: WEIDMANN ELECTRICAL TECHNOLOGY INC., VERMONT
Free format text: ASSIGNMENT OF ASSIGNORS INTEREST;ASSIGNOR:WEIDMANN DIAGNOSTIC SOLUTIONS INC.;REEL/FRAME:034830/0796
Effective date: 20150101
|Jan 13, 2017||FPAY||Fee payment|
Year of fee payment: 12